AS / NZS Installation and safety requirements for photovoltaic (PV) arrays; AS / NZS Structural Design Actions Part 2: Wind Actions; AS / NZS. The draft of amendments to AS/NZS Installation and safety requirements for photovoltaic (PV) arrays was released for public. The new AS/NZS has been released as of the 6th November and is applicable as of 6th February. (3 months from the date of its.
|Published (Last):||21 June 2008|
|PDF File Size:||11.4 Mb|
|ePub File Size:||7.60 Mb|
|Price:||Free* [*Free Regsitration Required]|
AC and DC installed in separate conduit and enclosures.
This article details the key updates and explains how they affect installers. This could lead to a potential hazard if the circuit is disconnected without adequate protection such as a load-breaking DC isolator.
In addition to this, AC and DC switchgear cannot share the same mounting rail, unless it is constructed from a non-conductive material.
Another requirement introduced in was the warning regarding DC isolators not de-energising the PV jzs and array cabling. Nonetheless, DC PV cables within a building, but not within these cavities, need to be protected with medium-duty MD conduit. However, please note that power limits and installation methods have been set for these product-specific requirements, so it is important that they are read carefully before using these products.
Powering the future for Australian sustainable transport.
For example, the labelling of conduit has been simplified from being required at each end and each change in direction, to being required bzs every 2 metres, consistent with the cabling labels. The revised HD conduit requirements will have a significant impact when PV systems are installed on sheds and commercial buildings, where cavities are not used to run DC cabling.
This means that measurements taken during commissioning are not to be displayed on these signs. However, the version of the standard provides clarification that reduces the need for installing these cages. The latest version of the standard has reduced the scope of this requirement, providing a more practical method of nzw the desired protection.
This is particularly useful for installing on roofs with small areas facing different directions. While fewer areas will now require HD conduit, the change may not have a significant impact on PV installations in the domestic market. A wholistic approach to long-term project success. In other areas ax a building, cabling is more visible and therefore there is a lower risk of damage.
Master Installer AS / NZS Update – Smart Energy Council
As Inspections Manager, Dan is responsible for the oversight of PV installation audits around Australia, including technical review of inspection outcomes aa the management and training of PV inspectors. To assist PV installers in keeping on top nzss changes in the industry, like these necessary standards updates, the Clean Energy Council has put in place a continuous professional development CPD program. DC-conditioning units and microinverters As previously stated, one of the key drivers of updates to the standard is the introduction of new products to the industry.
Furthermore, the labelling needs to be visible. For microinverter systems, displaying these ratings is generally not necessary as the voltage is usually the same as for other AC electrical systems VAC. SolarEdge power optimiser a DC-conditioning unit. It further specifies that the earthing cable from the array frame can be connected to the AC earth conductor at the inverter.
In addition, non-domestic buildings are permitted to be exempt from using HD conduit where ws installation method otherwise achieves the objective of minimising short-circuit risk.
This requirement was introduced with an aim to reduce the risk of short circuit by providing additional mechanical protection. Modules deteriorating over time can then compound the difference.
Global Sustainable Energy Solutions GSESwith its extensive experience in PV training, design and inspections, is regularly involved in discussions over practical methods that installers can use to implement the latest standards and guidelines. Cage installed by Solar Powered Homes to achieve restricted access. This is aa most effective way to achieve compliant insulation barriers between AC and DC circuits.
The previous standard only considered the scenario of a string of modules connected to a qs MPPT nzd therefore did not allow for the flexibility of these new products. This led to installers running 4 mm 2 earthing cables, independently, all the way from the array to the main switchboard.
It is not only clear that AC and DC need to be segregated, but insulation barriers have also been clearly specified as the means of segregation. After a challenging past five years, the electrical services industry is expected to experience For DC-conditioning units, the voltage and current displayed on the fire emergency information signs are to be equal to the maximum input ratings aw the inverter, consistent with sizing the load-breaking DC bzs.
It also further specifies that, where multiple arrays are installed, the voltage shall be the highest value present and the current shall be the sum of all array currents. A renewable energy certificate will only be given where a written statement is provided by the installer of the unit that the installation complies with the following standards. Solar installation standard – how the recent changes affect you.
Although using only UV-resistant HD conduit increases the cost of materials, it increases the durability of the system and may reduce the installation time. Season’s greetings Beamwidth testing for millimetre waves Telstra, Lexus to run connected vehicle field trial Trends in next-gen control room solutions Control room experts share their insights.
Although installing the correct labelling and signage is important, where they are displayed is also vital. However, in doing so, installers need to ensure that the earthing jzs will not be interrupted if the ss is removed and that the 50033 is of sufficient size according to the system rating and type. GSES has observed many PV systems installed since this update that have not included this warning, sometimes owing to the installer not being aware of the requirement or using up old-stock labelling kits.
The IP4X rating requires the barrier to prevent penetration of objects with a 1 mm diameter or greater. You will be required to comply with the following standards if you intend to design or install a solar photovoltaic system. A solar photovoltaic system is a unit that converts energy from sunlight into electrical energy.
Solar installation standard – how the recent changes affect you
This means that, if conduit is fixed to a wall, the solar labelling needs to be facing out. This will save installers a lot of work, especially if they are already using HD conduit and installing isolators within enclosures with lockable flaps. Top energy conference in Melbourne next week Australia’s most comprehensive clean and renewable energy event, All-Energy Australia, In these installations, it is now possible for the installation to be completed without HD conduit.